Experiment Hazard Class 9 – Electric and Magnetic Fields
This hazard classification applies to all experiments involving magnets, magnetic fields, and electric fields. Other hazard classifications such as electrical safety and their associated hazard controls may also apply to experiments in this hazard class.
Hazard Control Set
Controls – Persons with cardiac pacemakers or other medical devices that may be affected by magnetic or electric fields must be prohibited from entering areas where the steady state magnetic field exceeds 0.5 mT (5G) or the steady state electric field exceeds 1000 V/m. Barricades/warning tape as appropriate.
Procedural Controls – Safe work procedures to handle hazards should be developed. Shielding as feasible. Hand tools can become missiles in a sufficiently strong magnetic gradient, pinch hazards could be present; therfore limit personnel exposure. Only nonferromagnetic tools should be used in areas where the magnetic field may exceed 3 mT. Concerning Electric field strength greater than 5,000 V/m, eliminate ungrounded objects and/or use insulated gloves when ungrounded objects must be handled. Consult with ESQ-IH regarding safe work practices for work in electric fields that exceed 15,000 V/m
Design Reviews and Equipment Inspections – Medical Department must evaluate and counsel all employees with cardiac pacemakers or other medical implants
Signs and Labeling – Post areas where: Magnetic field exceeds 0.5 mt (5G), Electric field exceeds 1,000 V/M. Caution: DO NOT ENTER, Electromagnetic fields could be harmful to persons wearing pacemakers or other medical electronic implant. Signs are available through the AES ESH Coordinator 2-6714 or XSD ESH Coordinator 2-4192
Personal Protective Equipment – Electric fields that exceed 15,000 V/m require the use of protective devices (suits, gloves, and insulation).
Hazard Control ASSISTANCE
Consultation is available through the ESH Coordinators and EQO-IH. Please contact the local floor coordinators for arrangements.
Unless otherwise noted in the approved experiment safety plan, the Director of the APS Engineering Support Division delegates the authority to authorize an experiment in this hazard class to a member of the APS Experiment Review Board and any of the persons in the beamline personnel that appear in the list of Beamline Manager personnel authorized to approve experiments.
Hazard Control Verification
The Director of the APS Engineering Support Division delegates responsibility for verifying that required controls are in place to personnel delegated the authority to perform this task to the Experiment On-site Spokesperson and Beamline Management.
ANL LMS-Proc-234, Rev.0 Electric and Magnetic Fields
Reviewed May 01, 2013